The current consumption from the public power grid does not take place sinusoidal like with a conventional transformer, but more in pulses. This fact is reflected in the current draft of VDE-AR-N 41001. Point 184.108.40.206 refers to harmonic currents up to 9 kHz to be controlled. In addition to power generating systems, plants and storage facilities are also included. Measures to reduce harmonic currents - in particular the construction of filter circuits - should be coordinated by the customer in consultation with the network operator. Accordingly, it can be assumed in the future that permanent current measurements up to 9 kHz will be carried out across the board in low voltage.
GMW offers the full series of XCTB current transformers for measurements up to 20 kHz. These products guarantee high precision transmission up to 20 kHz on the one hand, and are designed to withstand the thermal demands of running in networks subject to harmonics on the other.
Output signals are 1 or 5 A, just like with the familiar inductive current transformer to IEC 61869-2. Performance data corresponds to standard values too. As a result, these transformers can also be used in conventional 50 Hz applications. An additional rating plate defines the frequency transmission behaviour.
Perfect for subsequent assembly into already existing installations. Easy and safe mounting. Due to the „click“-system even a one-hand mounting is possible. Available in nominal current ranges 100…1000 A. Deliverable with secondary current 5 A / 1 A. In total 8 different construction types of series XKBR. UL-certification in preparation and sealable. (XKBR 18S; XKBR 18L; XKBR 28; XKBR 42; XKBR42L)
Harmonic measurements with load 0.2 VA – Sr pf1 (power factor 1).
Suitable for networks subject to harmonics with fundamental frequency of 50 Hz.
Perfect for subsequent assembly into already existing installations. Easy and safe mounting, due to hearable locking system. Available in nominal current ranges 250…2500 A. Deliverable with secondary current 5 A / 1 A. Accuracy classes @ 50 Hz: 1 and 0.5- Four different construction types. Connecting cable for harmonic measurements: HELUKABEL. type: OZ-500 HMH-C with 2x2.5 or 2x4 mm² (0-10m). Harmonic measurements with load 0.2 VA – Sr pf1 (power factor 1). Suitable for networks subject to harmonics with fundamental frequency of 50 Hz.